Daily maintenance of vertical turbine fire pump
1. Check the oil level of the fuel injection pump governor
If the oil level of the fuel injection pump governor does not reach the prescribed engraved mark, it should be added in time, and the upper limit should not be exceeded.
2. check the oil level in the oil pan
The maintenance personnel should observe whether the oil level has reached the scale mark on the oil scale. If there is a shortage, add it to the specified in time, but do not add too much, and cannot exceed the upper limit of the scale mark.
3. Check whether there is sufficient lubricating grease in the oil filling point of the water pump
4. Check whether the water in the water tank is sufficient
The maintenance personnel should regularly check whether the water in the water tank is sufficient. If the shortage is found, it should be refilled in time. Special attention should be paid to that the added water should be clean fresh water. If it is directly added to groundwater, it is likely to form scale in the water tank. It will affect the cooling effect and even cause malfunctions. Of course, it can be used after the groundwater is softened. Special attention should be paid to the low temperature in the north. It is necessary to equip the appropriate antifreeze according to the local temperature.