Installation points of pipeline centrifugal pump
Common fault analysis and treatment method of pipeline centrifugal pump
Affecting the pump flow is mostly the suction pipe leakage, bottom valve leakage; water inlet blockage; bottom valve into the water depth is not enough; pump speed is too low; sealing ring or impeller wear is too large; suction height exceeds the standard, etc. Check the suction pipe and bottom valve, block the source of air leakage; clean the silt or blockage at the water inlet; the depth of the bottom valve into the water must be greater than 1.5 times the diameter of the inlet pipe, increase the depth of the bottom valve into the water; check the power supply voltage, improve the pump speed, replace the sealing ring or impeller; reduce the installation position of the pump, or replace the high head pump. Power consumption is too high pump speed is too high; pump spindle is bent or pump spindle and motor spindle are not centered or parallel; choose pump head is not suitable; pump inhalation mud and sand or blockage; motor ball bearing is damaged, etc. Check the circuit voltage, reduce the pump speed; correct the pump spindle or adjust the relative position of the pump and the motor; choose the pump with suitable head; clean the mud and sand or blockage; replace the ball bearing of the motor.
The pump body vibrates violently or produces noise The pump is not installed firmly or the pump is installed too high; the motor ball bearing is damaged; the pump spindle is bent or is not centered or parallel to the motor spindle, etc. Install the pump steadily or lower the installation height of the pump; replace the motor ball bearing; correct the bent pump spindle or adjust the relative position of the pump and the motor.